A medical supply manufacturing facility in Boston, MA encountered issues with its 17-year-old chiller, stemming from leaks in the chiller’s condenser coil. The facility and its managing company contacted HTS to service the chiller and repair the problem. After conducting a full investigation and inspection of the system, the HTS service team determined that the best course of action was to replace one of the condenser coils.
This solution was easier said than done. The 1,000 pound, 4 ft. by 30 ft. coil had to be removed from the existing unit, with less than an inch of open space on each side. From 50 yards away, HTS’ service team guided and directed a 40-ton crane as it carefully removed and replaced the coil.
HTS Service overcame these challenges to complete the project in a time frame of three days, and deliver a solution that had the facility’s circuits back online as quickly as possible to minimize downtime.